The Cascadian ICS-SI Sediment and Iron Water Filter System
The Cascadian ICS-SI sediment and iron water filter systems filter sediment and remove, iron and manganese from your water. This is not the same as PolyHalt based iron treatment. With PolyHalt based treatment clear iron is forms an ion bond and is prevented from converting to colored iron but remains in the water. The ICS-SI actually traps and removes iron and manganese from the water. The ICS-SI is an excellent treatment for well water and anytime you want the iron actually removed.
Sediment and iron filter system details:
Compared to traditional sediment and iron filter treatment systems the ICS-SI sediment and iron filter is
Fits almost anywhere
Lower cost to buy, ship and install
Simpler to maintain.
Does not require oxidation, the addition of chlorine, or chlorine removal as with traditional iron filters.
Works over a wide pH range.
Eco-friendly; No salt or power required. Produces no waste water.
Includes drain on filter housing for clean no spill easy filter changes.
If you want to add PolyHalt Salt Free Softening to the ICS-SI check out the ICS-SIP.
ICS-SI Sediment and Iron (Removal) Water Treatment System
Dimensions: 29″ x 15.5″ x 8″ (Height x Width x Depth)
Connection Diameter: 1” System Drain: 1/2″ Max. Capacity: 12 Months Max. Flow: 15 gpm Min. Pressure: 25 psi
Max. Pressure: 120 psi Min. Temperature: 39° F Max. Temperature: 113° F Number of Filters: 2 Weight: 33 pounds dry Filter Housing Drain Included
Bacteria: None Allowed Chlorine: NA Colloidal Iron: NA Hardness: NA Hydrocarbons, oils, or lubricants: None Allowed Hydrogen Sulfide: None Allowed (use ICS-H to remove) Iron & Manganese (Clear Only): <3 ppm Iron & Manganese (Colored): <1 ppm Iron Bacteria: None Allowed Organic Iron: None Allowed
pH: Between 7.0 and 8.5 Sediment: >5 micron Silica: NA Tannin / Organics: None Allowed Turbidity: Less than 1 NTU
Notes for all ICS systems:
DO NOT INSTALL ON WATER THAT IS MICROBIOLOGICALLY UNSAFE
If Raw Water Parameter Condition for Operation = “NA” the systems will not affect and is not affected by concentrations of that parameter typically found in drinking water
If Raw Water Parameter Condition for Operation = “None Allowed” Remove through adequate pre-treatment
If Raw Water Parameter Condition for Operation = “Not for extreme levels” The cartridge useful life may be shortened and require more frequent replacement.
Extreme levels of any parameter may shorten useful cartridge life
Stated “Max Capacity” may be reduced by overall raw water chemistry
Complete treatment with the ICS-SI is a two-step process.
Step 1. Water first passes through a multimicron sediment filter to reduce visible sediment and particles. This filter a specially designed high sediment holding capacity for long life with lower pressure drop and is not susceptible to microbiological growth.
Step 2. Water passes through a filter designed to remove iron and manganese. This is not ionic bonding to solve iron and manganese problems but a process that actually traps and filters iron and manganese from the water.